Drop-In Refrigeration System Installation & Operation ManualLow Ambient Wiring Diagram - 0ºF LOW AMBIENT ACCESSORY INSTALLATION INSTRUCTIONS MODELS 2LA04700100 GENERAL The Electronic Low Ambient Controller 2LA04700100 is designed to regulate condenser head pressure at low ambient temperatures by varying the amount of air-flow through the condenser. It helps to ensure sufficient 7 1 035-16720-000 Wiring Diagram, 3-6 ton 8 1. Installation and Maintenance Instructions Refer to the attached wiring diagram. Low Ambient Kit Kit #ALOAMB505-1. Page 2 of 4 Issue 0837 506161-01 7. Wire the low voltage control wire for the fan relay as to the attached wiring diagram. 8. Reinstall the cooling chassis.. Low Ambient Control - LAC (Includes mounting screws, tape and temperature probe) 2 1 035-13207-000 Kit Instruction Form 3 1 AB020BLU7171700 Wire, 700/BLU [from LAC (3 or 4) to M1 (T2)] 4 1 AB022BLK7171701 Wire, 701/BLK [from LAC (2) to M1 (T1)] 5 1 AB020YEL7171808 Wire, 808/YEL [from LAC (5) to M1 (COIL A)] 6 1 AB022BRN7157809 Wire, 809/BRN [from LAC (6) to M1 (COIL B)] 7 1 035.
the low ambient control wires between the terminal block and T2 of the compressor contactor. Step 9. Remove the service port caps on the suction and liquid lines. Install the low ambient control and the high pressure switch on the liquid line with the flare tee adapter that is brazed to the controls. Install the low pressure switch on the suction line.. This is the Hvac Low Ambient Control (Pressure Switch) – Youtube of a picture I get off the Low Pressure Ac Switch Wiring collection. You can save this pics file to your own pc. Please right click on the image and save the photo.. The Low Ambient Control Kit is designed for use in air-conditioner and heat pump products. The kit consists of a pressure switch, a service adapter tee, a 24V relay for heat pump applications, and miscellaneous parts for.
If unit wiring diagram is not available or Low ambient pressure switch S11 is wired in series with does not show the low ambient kit, refer to appropriate outdoor fan relay or compressor contactor (single-stage wiring diagram in figures 3 through 13 for wiring or speed units).. 8 Low Ambient Control Kit 1. IO Module Installation Method Installation Method ① Separate front panel from outdoor unit. ② Separate front cover of control box. ③ Assemble IO Module and bracket. ④ Connect the connection wires according to the instructions. (Please refer to Setting and Using Method) ¸ ¹ º + » Main board connector CAUTION. • Low Ambient - An integrated low-ambient control allows all units to operate in the cooling mode down to 0 F outdoor ambient without additional assistance..
Low Pressure Switch Bypass, Low Ambient Startups, 18-240 VAC • Knob adjustable from 10-1,000 seconds • Ideal for “winterstart” kits WIRING DIAGRAM Input 18-240 VAC 1 2 3 Load MODE OF OPERATION INSTALLATION SPECIFICATIONS Input wiring diagram below. 3. Select the desired time delay. 4. Reapply power, check operation.. The Low Ambient Control Kit is designed for use in single package air-conditioner and heat pump products. The kit consists of a pressure switch, a service adapter tee, a 24V relay for heat pump applications, and miscellaneous parts for mounting. The kit is intended to maintain system pressures at normal levels should cooling be required at low. included. Affix the low ambient kit wiring diagram on the control box door next to the unit wiring diagram. LAKT01 (3 thru 6 tons) Wiring Diagram 0140M00108 - use with AC and HP units, three phase and single phase application. For residential 3 phase condensers, connect wires per.
Low Ambient Kit BAYLOAM103 BAYLOAM103 BAYLOAM103 BAYLOAM103 Refrigerant Lineset 5 TAYREFLN9*TAYREFLN7* TAYREFLN9* TAYREFLN7* 1 Certified in accordance with the Air-Source Unitary Heat Pump equipment certification program which is based on AHRI Standard 210/240.. CGAM / CXAM Fan wiring diagrams. Model number description. Digit 12 = Efficiency level. Digit 41 = Sound package. Digit 15 = Operating map. Digit 24 = Heat recovery. 1 = Standard efficiency. C=Low ambient. 3 = Total heat recovery. D=Wide ambient. G= Medium-low ambient. H= Medium-high ambient. Unit type. Sizes. DIGIT 12. DIGIT 15. DIGIT 24.